A major advantage of HDPE pipe is its availability in continuous lengths on a reel, or in a coil, for a wide range of
diameters (normally 6-inches or possibly greater). For HDPE products not available in continuous lengths, discrete lengths of
HDPE pipe may be readily fused in the field, without an appreciable loss in the tensile capability required for HDD
pulling operations.(ASTM International D 2657) In the latter case, the pipe should be assembled prior to the pullback operation to
maintain continuity during the pipe placement process and avoid unnecessary delays. Significant interruptions may
lead to increased drag and resulting pulling forces, including eventual loss of integrity and collapse of the bore
hole, preventing further movement of the pipe.
ASTM International F1962 (Standard Guide for Use of Maxi-Horizontal Directional Drilling for Placement of Polyethylene Pipe or Conduit
Under Obstacles, Including River Crossings) and PPI TR-46, (Guidelines for Use of Mini-Horizontal Directional Drilling
for Placement of High Density Polyethylene Pipe)
provide information regarding connecting the HDPE pipe to the drill
rods for pull-back, including associated hardware:
- Breakaway Link
The following procedures should be followed when during the pipe pull-back operation:
- Avoid supporting pipe on surface that may cause abrasion during pullback
- Minimize back tension on pipe, to prevent escalating effects at pulling end
- Avoid pulling around sharp bends (tighter than allowable bending radius), to avoid pipe collapse (kinking).
Thus, it is important to minimize bending of the pipe as it enters the bore hole, and to ensure low friction on the
portion of the pipe outside the hole. This may be accomplished by the use of appropriate lifting equipment and roller
stands to reduce friction. Due to the potentially high tensile load at the pipe exit, it is especially important to
avoid sharp bends at this point.
HDPE pipe has a very tight safe bend radius. This feature allows pipe to be strung on the ground in configurations
impossible to do safely for other types of pipe. Instead of blocking cross streets the pipe is often laid down by simply
bending it around the corner. For example a 12" HDPE pipe may be safely bent to a radius of only 28 ft, which allows this
pipe to be placed in a typical cul-de-sac without fittings. In addition, HDPE pipe will almost always have a tighter
bend radius than the drill stem being used for installation. This provides an extra safety factor against damaging
the pipe by bending in the bore.
Product Pipe Support at Pipe Entry
(Source: Trenchless Engineering Corporation)